DOWNPATRICK COURTHOUSE 21 ENGLISH STREET DOWNPATRICK BT30 6AD
Condition Items 1-3 Contractor has confirmed compliance with these items. Condition Item 4 Please see below methodologies for works being completed by the Contractor and attached safety data and product information sheets. Regarding cleaning (item 4): “See below method of how the cleaning works will take place at Downpatrick courthouse • Areas to be worked in will be pre-sprayed with Bio side working from the ground up – (data sheet attached of product to be used) • Upon completion of the spraying the areas will be steam cleaned rinsed down • Upon completion we will return and rinse down the building • Carry out a final biocide spray of the site • Paint work to base to be removed in preparation for new“ Regarding rendering works: “Regarding the repairs to the external masonry, as your aware this has been highlighted as stone repairs by the consultants and it appears to be areas that have had lime render applied. To progress these works I would propose stripping the defective areas back to the original structure. The method of building the render up would be carried out using the following method • Chip back defective plasterwork • Remove dust from original building fabric • Scud the wall with a lime slurry (nhl 3.5)to provide a key to receive next stage • Apply a lime scratch coat (using nhl 3.5) • Apply lime plaster float coat (using nhl 3.5) • Take in faux blockwork bonds” Condition Item 5 Please refer to Contractors Job Card attachment for sample areas carried out by the Contractor. I have already visited site with Nicola Golden (HED) to show sample areas in person. No stone replacement, re-rendering or paint finish works have yet been carried out as the building requires cleaning first. If samples of these are required I would propose we obtain your consent to complete the cleaning, and provide further contact in due course regarding a sample area.