5 - 10 Great Tower Street London EC3R 5AA
Submission of (a) Fully detailed design and layout drawings for the proposed SuDS components including but not limited to: attenuation systems, rainwater pipework, flow control devices, design for system exceedance, design for ongoing maintenance; surface water flow rates shall be restricted to no greater than 2 l/s from each outfall and from no more than two distinct outfalls, provision should be made for an attenuation volume capacity capable of achieving this, which should be no less than 90 m3; (b) Full details of measures to be taken to prevent flooding (of the site or caused by the site) during the course of the construction works; and (c) Evidence that Thames Water have been consulted and consider the proposed discharge rate to be satisfactory pursuant to condition 13 of planning permission 23/01254/FULMAJ dated 07/06/2024.